Electrical power requirements
Each system requires eight separately protected power circuits, with eight power drops for each system (four drops for the compute rack and two drops for the storage rack).
The power requirements for each circuit are listed in the following table.
Important: Ensure that the power supplied to the rack is uninterruptible.
|Total plugs (Drops)||8|
|Voltage||200 - 240 VAC, 50 Hz/60 Hz (Single Phase)|
|Circuit Breaker Rating||32 Amps (Single Phase)||30 Amps (Single Phase)||32 Amps (Single Phase)|
IEC 309 32A P+N+G
NEMA L6-30 2P+G
Clipsal 32A 2P+G
|Power Drop Length||
8 ft (2.5 m) out top of rack
5 ft (1.5 m) out bottom of rack
|Maximum Power||13,700 W|